Locate your stop and waste or shut off valve.
This is the access point for a stop and waste at this residence.
This is a simple gate valve in a crawl space. (This shut off was leaking and had to be repaired before the system could be turned on. It is shown here as an example that all systems are not installed with a stop and waste).
This is a regular ball valve that is located in the crawl space of a home.
If there is a backflow on the property, I will generally shut it off before I turn on the stop and waste or main shutoff. The two handles on this backflow are the #1 and #2 shutoff. If the handle is pointing the same direction as the pipe, the valve is open. Alternately, if the handle is turned so that it faces across the pipe, the valve is closed.
Slowly turn the water on by twisting / turning in a counterclockwise direction. Note, a stop and waste only turns 1/4 turn.
Use the first little valve (called a Test Cock) to flush any debris from the line so they do not get caught in the backflow. You open the test cock using a flat head screwdriver.
Turn the #2 shutoff slightly on so the system can fill slowly.
Locate the sprinkler valves / sprinkler boxes on the property.
Shut off any open drains or open hose bibs.
Set all the valves on the property to the closed position. This is done by turning the solenoid (Yellow arrow) and the bleed valve (Red arrow) clockwise until they are snug. Be careful not to over tighten these as they are just plastic threads and are prone to breaking if over tightened. Be patient, it may take a few seconds or up to a minute for all the valves to shut down.
If you prefer, you can shut all of the valves down first. It is simply my preference to shut the valves down after I start charging the system. This comes from my experience with large sprinkler systems, allowing air to escape the system before pressurizing.
On most valves the center stem is actually a flow control, it is not intended to be used to turn the valve on or off. This is used to reduce or control the amount of water flow Through the valve.
Once the system is fully pressurized, open the #2 shutoff fully, and leave it in the open position for the remainder of the watering season.